Tri - Level Dimming Control , AC Motion Sensor Switch , Daylight
Used together with ordinary 1~10v dimmable driver, achieve
tri-level dimming control. When sensor is triggered, the lamp will
be 100% on, after the Hold-time, the lamp will drop to pre-set
dimming level, after a further long absence of people(Stand-by
period), the lamp will completely switch off.
5.8GHz C-band microwave motion sensor, tri-level dimming control.
Input voltage: 120〜277V AC, 50/60Hz.
Rated load: 400W@120VAC (capacitive)
800W @ 200〜277VAC (capacitive)
Stand-by power: <1w.
Dual-processor technology, real Daylight monitoring function for
Zero-cross point operation, protect the sensor relay against the
in-rush current, secure the max. load and life time of the relay.
Detection range up to 12m in diameter.
Mounting height: 3~6m.
Operation temperature: -20℃~ +70℃
IP rating: IP20.
Detection range can be reduced by selecting the combination
on the DIP switches to fit precisely each application.
Hold-time means the time period to keep the lamp on 100% after
*when hold-time set as 3s, sensor enters into test mode, this test
mode is mainly for users to choose the desired detection range. In
this mode, the daylight sensor is disabled, when there is no
motion, fixture keeps off, when there is motion detected, fixture
keeps a cycle of 3s on and 2s off.
Daylight sensor means the daylight threshold to enable or disable
the sensor function.
"Disable": The sensor works always, even during daylight.
"50lux": The sensor works only in twilight.
"10lux, 2lux": The sensor works only in the dark.
This is the time period that the lamp remains at a low light level
before it is completely switched off in the long absence of people.
“+∞”: means bi-level dimming control, the fixture never switch off.
Stand-by dimming level
This is the dimmed low light level you would like to have after the
hold-time in the absence of people.
*0% means on/off control.
10%--Vdim=1.5Vdc 30%--Vdim=3.0Vdc 50%--Vdim=5.0Vdc
Daylight monitoring function--
Utilizing the Dual-processor technology, this sensor can tell the
difference of natural light and artificial light(lamp) from behind
the diffuser, switch on automatically(even without movements) when
the ambient light is below target value, and then switch off
automatically whenever the artificial light is not required(ambient
light is bright enough).
This is the REAL & INTELLIGENT daylight monitoring sensor for
Note: Lux-Off sampling time---30s; Lux-On sampling time---10s.
Lux-On function takes effect only when standby dimming period set